A large Midwestern Engine Manufacturer requires wastewater treatment of spent cleaners for process steps. Oil and grease loading is in both emulsified and insoluble forms.Read the full post
- OMEGA AP-2210 is an anionic polyelectrolyte in emulsion form.
- OMEGA AP-2210 will react quickly at a pH level of 7 to 12 to flocculate metal hydroxides.
- A rapidly formed dense floc, of large size and agglomeration, provides for immediate settling in clarifiers and holding basins.
- OMEGA AP-2210 is a very effective as a sludge conditioning agent.
- Metal hydroxide is tightly bound to the polymer lattice structure resulting in a high tolerance for mixing and shear resistance.
Type: Anionic polyelectrolyte
Form: Liquid concentrate
Charge: 32% charge density
Molecular Weight: Medium
Appearance: Opaque white liquid
Odor: Hydrocarbon odor
Viscosity: 0.5% solution is 500 cps @ 20° C
Density: 981 gm./l (8.18 lb./gal.)
|Dosage Range and Feed Methods||
The OMEGA AP-2210 dosage will range from 0.5 ppm to 15 ppm depending upon solids composition and particle charge differential.
Dilutions of OMEGA AP-2210 are required to fully activate the polymer concentrate.
A solution of OMEGA AP-2210 should be diluted with water to a 0.1% to 02% solution strength.
Dilutions of OMEGA AP-2210 should be agitated via a mixer for a period of 20 to 30 minutes.
Tanks of plastic or lined mild steel composition are compatible. Pumps of plastic or any non-metal composition are compatible.
Application in the point of high turbulence will maximize performance. The use of a rapid mixer after the addition of OMEGA AP-2210 will further promote floc size and agglomeration.
|Safety and Handling||
OMEGA AP-2210 is a non hazardous material. Use appropriate safety equipment to prevent eye and skin contact. If contact does occur, wash with water. If eye irritation develops, seek medical attention.
|Container Size and Shipping||
OMEGA AP-2210 is available in 275 gallon totes, 55 gallon drums, and 5 gallon containers
EU sizing : 1040 Liter totes, 208 Liter drums, and 18 Kg containers
Spills of OMEGA AP-2210 are very slippery and should be localized and contained with absorbent material. As with any chemical application for waste treatment, conform to all applicable regulatory criteria.
The information presented herein has been compiled from sources considered to be dependable and is accurate to the best of the sellers knowledge. However, seller makes no warranty whatsoever, expresses, implied, or of merchantability regarding the accuracy of such data or the results to be obtained from the use thereof. Seller assumes no responsibility for injury or to third persons or for any damage to any property and buyer assumes all such risks.<< Go Back